Your Result is copied!

ADVERTISEMENT

Enter the required parameters to precisely calculate “Box Fill" requirements for an electrical wiring box.

Add this calculator to your site

ADVERTISEMENT

ADVERTISEMENT

This box fill calculator precisely estimates the total box fill volumes for electrical utility boxes, prioritizing safety and electrical system reliability in various installations.
By using this tool, you can easily determine the perfect dimensions for your electrical boxes, ensuring they meet the safety standards of the National Electrical Code®.
**What Is Box Fill Calculation?**

It is the calculation of the combined volume occupied by conducting wires, grounding wires, and other components in an electrical utility box.
The main objective of this box fill calculation is to prevent overcrowding in electrical boxes because an overloaded box can result in faults, arcing, or even pose a risk of fire.
**How To Calculate Box Fill?**

Follow the below-mentioned steps to calculate box fill:
**Identify Components: **

**Assign Values:**

**Apply Multipliers:**

**Calculate Box Fill:**

**Conductor Fill:**

**\(\ A_w =\ n_w\)**
And
**\(\ V_w =\ A_w\times \ V_{largest\ conductor}\)**
Where
In the following table we have provided the conductor wire size and their allowance volumes. For ease, use our wire size calculator and optimize your wire size assessments.

Source Better Homes & Gardens
**Clamp Fill:**

**Support Fittings Fill:**

**Device or Equipment Fill:**

**\(\ A_d = 2 * n_d\)**Where
**\(\ V_d =\ A_d\times \ V_{largest\ conductor}\)**
Where
**Equipment Grounding Conductor Fill:**

**The Total Box Fill Volume:**

**\(\ V_{total} =\ V_w+V_c+V_s+V_d+V_g\)**
If the largest conductor is equal to the largest grounding wire size then find the total volume allowance and multiply it by the free space required for the largest conductor.
**\(\ A_{total} =\ A_w+A_c+A_s+A_d+A_g\)**
**\(\ V_{total} =\ A_{total}\times \ V_{largest\ conductor}\)**
Where
**Example:**

Suppose you have a box with 10 wires, where the largest conducting wire size is 12 AWG, the number of devices is 5, and there are 10 grounding conductors with the largest grounding wire size being 12 AWG, determine:
**Solution:**
Given that:
Largest conducting wire size = 12 AWG = 2.25 cu inches
Number of conducting wires = 10
Devices = 5
Grounding conductors = 10
Largest Grounding conductor wire size = 12 AWG = 2.25 cu inches
\(\ A_w =\ n_w\)
\(\ A_w =\ 10\)
**Conductor Fill Volume:**
\(\ V_w =\ A_w\times \ V_{largest\ conductor}\)
\(\ V_w =\ 10\times \ 2.25\)
\(\ V_w =\ 22.5\)
**Device Fill Volume allowance:**
\(\ A_d = 2 * n_d\)
\(\ A_d =\ 2\times \ 5\)
\(\ A_d =\ 10\)
**Device Fill Volume:**
\(\ V_d =\ A_d\times \ V_{largest\ conductor}\)
\(\ V_d =\ 10\times \ 2.25\)
\(\ V_d =\ 22.5\)
**Equipment Grounding Fill Volume Allowance:**
\(\ A_g=\dfrac{n_g}{4}\)
\(\ A_g=\dfrac{10}{4}\)
\(\ A_g=\ 2.5\)
**Grounding Wire Volume:**
\(\ Largest\ Grounding\ Wire\ Size =\ 12\ AWG\)
\(\ Grounding\ Wire\ Volume =\ 12\ AWG =\ 2.25\ cu\ inches\)
**Equipment Grounding Fill Volume:**
\(\ V_g =\ A_g\times \ V_{largest\ ground\ Wire}\)
\(\ V_g = 2.5*2.25\)
\(\ V_g =\ 5.625\ cu\ inches\)
**Total Volume Allowance Needed:**
\(\ A_{total} =\ A_w+A_c+A_s+A_d+A_g\)
\(\ A_{total} =\ 10+0+0+10+2.5\)
\(\ A_{total} =\ 22.5\)
**Total Box Fill Volume:**
\(\ V_{total} =\ V_w+V_c+V_s+V_d+V_g\)
\(\ V_{total} =\ 22.5+0+0+22.5+5.625\)
\(\ V_{total} =\ 50.625\ cu\ inches\)
Ensure precision by cross-checking your manual calculations with our electrical box fill calculator and optimize your results for a safe electrical system.
**The Importance of Electrical Box Fill Calculation:**

The box fill calculations are very important in electrical installations for many reasons, including:
**FAQ’s:**

**How Many Wires Can I Put In An Electrical Box?**

A standard single-gang box has 18 cubic inches of space, which can contain:
**Do Grounds Count In Box Fill?**

Yes, the grounding wires are also included in calculating box fill volumes. According to the NFPA 70: National Electrical Code® 2020, a single volume allowance is specified for one to four equipment grounding conductors or equipment jumping conductors. Every additional grounding conductor needs an extra 1/4 volume allowance.
**What Is The NEC Code For Box Fill?**

The box fill code, outlined in NEC 314.16 states that the boxes and conduit bodies must have the appropriate approved size to provide free space to all the enclosed conductors. The volume of the box calculated as per 314.16(A) should never be less than the fill calculation as determined in 314.16(B) in any case.

- Determine the number of conductors (wires) and their volume
- Recognize the device (switches, receptacles, etc.) that you have to install in the box
- Count any internal cable clamps, luminaire studs, or other fittings

- Every conductor is considered one
- All the devices have a specific value, mostly two

- Multiply the total number of device mountings by the values specified in NEC Table 314.16(B)

- Put these values in the formulas to calculate the fill volume of each component and sum all the fill volumes to find the right box size

- \( A_w\) is the conductor fill volume allowance
- \(\ n_w\) represents the number of conducting wires
- \( V_w \) is the conductor fill volume
- \( V_{largest\ conductor}\) is the free space we provide for the largest conductor

Size of Conductor (AWG) |
Volume Allowance Required Per Conductor (in.³) |

18 | 1.5 |

16 | 1.75 |

14 | 2 |

12 | 2.25 |

10 | 2.5 |

8 | 3 |

6 | 5 |

If you are using an electrical box with internal clamps, then:
**\(\ A_c=\ 1\)**
Otherwise (no clamps):
**\(\ A_c=\ 0\)**
**\(\ V_c =\ A_c\times \ V_{largest\ conductor}\)**
where

- \(\ A_c\) is the clamp fill volume allowance
- \(\ V_c\) is the clamp fill volume

If there are one or more luminaire studs or hickey inside the box:
**\(\ A_s=\ 1\)**If there are no luminaire studs or hickey inside the box:
**\(\ A_s=\ 0\)****\(\ V_s =\ A_s\times \ V_{largest\ conductor}\)**where

- \(\ A_s\) represents the support fittings fill volume allowance
- \(\ V_s\) is the support fittings volume

- \(\ A_d\) is the representative of the device fill volume allowance
- \(\ n_d\) is the number of devices

- \(\ V_d\) is the device fill volume

If 1–4 grounding conductors that are entering in the electrical box,**\(\ A_g=\ 1\)**
If 5 or more:
**\(\ A_g=\ 1+\dfrac{n_g−4}{4}\)**
or
**\(\ A_g=\dfrac{n_g}{4}\)**
Where
**\(\ V_g =\ A_g\times \ V_{largest\ ground\ Wire}\)**
Where

- \(\ A_g\) is the representative of the grounding conductor fill volume allowance
- \(\ N_g\) is the total number of grounding conductors

- \(\ V_g\) shows the equipment grounding conductor fill volume
- \(\ A_g\) represents the grounding conductor fill volume allowance
- \(\ V_{largest\ ground\ Wire}\) is the free space

- \(\ V_{total}\) is the total box fill
- \(\ A_{total}\) represents the total volume allowance
- \(\ V_{largest\ ground\ Wire}\) is the free space as defined in Table 314.16(B)

- Grounding wire volume
- Equipment grounding fill volume
- Total volume allowance needed
- Total box fill volume

**Preventing Overcrowding:**It prevents overheating, increased fire hazards, and potential damage to electrical components**Compliance with Regulations:**Helps to comply with the National Electrical Code (NEC) regulations, ensuring that the installations meet the necessary codes**Enhancing System Reliability:**Using the box fill calculations, you can form reliable electrical systems**Safety:**It's the electricians' main concern and can be achieved easily with the help of this calculation that they can perform manually or by using a box fill calculator.

- 9 #14-gauge wires
- 8 #12-gauge wires
- 7 #10-gauge wires

**Support**

**Email us at**

© Copyrights 2024 by Calculator-Online.net